|Deka Unigy II Series 6AVR95 |
Cat. No. MK-6AVR95-15
Container Material: Standard
Polypropylene – This material is typically used when there are no
requirements for a flame retardant material. Add “S” suffix to module
number when ordering. (ex. 6AVR95-07S) Flame Retardant Polypropylene
(Optional) – This material is a V-O halogenated polypropylene. This
material has an LOI (Limiting Oxygen Index) of greater than or equal to
28%. Add “L” suffix to module number when ordering. (ex. 6AVR95-07L)
Termination: Top or side
termination is available as a standard feature at no additional cost.
Module Size: There are various
module sizes, a 6-cell module for 7 thru 15 plate cells and a 3-cell
module for 17 thru 33 plate cells. These module sizes are our most
popular configurations. For special space requirements, there are two
additional sizes, a 4-cell module for 7 thru 15 plate cells and a
2-cell module for 17 thru 33 plate cells. It offers more choices in
configuring the battery system, provides more flexibility when
selecting height and lengthof your particular system configurations,
and enhances overall space saving and versatility.
Maximum Modules: Modules can
be stacked from one module high all the way up to eight modules high
and still meet UBC 97 seismic zone 4 standards (using a one-piece base).
Connector Package: Our standard connector package meets
discharge rates as low as the one hour rate to 1.75 vpc. Optional
packages are available to provide the proper hardware for your higher
Base Support: The standard
base support is made up of two pieces, a left and a right side support.
It is UBC 97 certified up to and including seismic zone 3 faultline.
(For details on optionalOne-Piece base, see below
| Length 2
|| Depth 3
|| Height 4
|| 37.00" (940)
|| 9.54" (242)
|| 715 lbs. (324)
|1 Add “S,” for Standard
Polypropylene, or “L,” for Flame Retardant
Polypropylene, suffix to module number. (ex. 6AVR95-07S)
2 For system length take
dimension and multiply by number of
stacks. For side termination add additional 6" (3" per side).
3 Includes front shield.
Add additional .75" for one-piece base.
|4 For module stack height, subtract
1.5" from height and
multiply by number of modules and then add 1.5."
For overall battery height (top termination) add 4" for base,
1.5" for terminal bracket and 6.25" for top shield.
5 Weight includes module +
cells, but not the cell hardware